Foam liquid storage knowledge -- Quanzhou foam liquid elected Chuan 'an
Date：2021-08-26 16:57:40 | Browse：6
Generally speaking, after the foam liquid enters the site, it needs to be sampled on site for future inspection when necessary. In the case of large amount of foam liquid, it is necessary to send it to a qualified testing unit for testing. The foam solution should be checked under one of the following conditions: The design dosage of 6% low-expansion foam solution is greater than or equal to 7.0t. The design dosage of 3% type low-expansion foam solution is greater than or equal to 3.5T. The lower limit reserve of foaming fluid in 6% protein type is greater than or equal to 2.5t. The lower limit reserve amount of multiple foam liquid in 6% synforming is greater than or equal to 2.0t. The lower limit reserve of high-expansion foam liquid is greater than or equal to 1.0T. The foam liquid that needs to be sampled on site and sent for inspection as stipulated in the contract documents.
The foamed solution shall be stored in an environment free from direct sunlight or any heat source. The product shall be kept within the recommended temperature range, which is usually indicated by the manufacturer of the foamed solution in the relevant product information. In addition, the storage environment shall be free from the possibility of flooding. Keep track of the foam batch number and ensure that the foam produced earlier will be used first. The color of the foam solution may vary slightly from batch to batch, and the color may change with the aging process. In general, different types, different brands and different types of foam liquid can not be mixed without experimental proof. However, the same type of foam can be used in combination with the same type of foam liquid with the same performance and quality in certain emergencies requiring immediate use of foam liquid. If the amount of foam liquid in the container is found to be low, it is important to contact the foam liquid manufacturer for support before replenishing the container. Foam extinguishing agent should be stored in a ventilated and cool place at a temperature lower than 45oC, which is higher than its low operating temperature. Stored in accordance with the storage conditions of this standard or the storage conditions required by the manufacturer.
Quanzhou foam liquid manufacturer which better - chuan Ann fire industrial co., LTD., sichuan fire fighting products have pressure proportional mixing device, foam extinguishing agent, foam generator, portable foam extinguishing equipment, foam gun, foam spray, foam fire hydrant, bubble switch box, wet alarm valve, deluge alarm valve, preaction device, water flow indicator, sprinkler, fire pump adapter, fire hydrant box, etc. Welcome new and old customers to call details, Chuan an dedicated service for you.